Drainage at Rafee Hotel, off A46 near Thrussington
Posted on 25th August 2017 at 12:01
We been have appointed by Rafee Hotel (with over 50 rooms) to investigate into foul drainage problem which served the laundrette facility area.
Following CCTV drain survey by EMD, it was discovered the existing foul drainage had flat spots beneath the facility building with no confirmed connection point. The waste water seeping away under the foundations of the building leading frequent smell and blockage problem.
Having designed foul drainage which serves 3 internal foul connections from the facility room and gravity feed connection into nearby septic tank. A adequate pipe size to achieve minimum self-cleansing velocity that has been installed with trap to prevent smell backing from the septic tank. Happy customer with permanent drainage solution fixed.
Share this post: